WITH MEASURABLE RESULTS
HydraTite® (Internal Joint Seal System)
HydraWrap® (Fiber Reinforced Polymer)
Power & Utilities
A 102” Prestressed Concrete Cylinder Pipe (PCCP) that was part of a recirculating cooling water line at a fossil fuel power generation station had begun to show signs of aging. A joint had become separated and was visibly deteriorated. During the inspection, broken and missing portions of mortar were found.
Cement-based filler was placed in the joint and the surface of the pipe leading up to the joint was prepared with a wire wheel. Then the HydraWrap epoxy was applied to the joint and allowed to cure. The EPDM rubber was placed over the joint and the retaining bands expanded into place. The seal was then air tested.